A/C Solutions Heating & Air Conditioning provides heater and air conditioning repair, service, installation and services in Sugar Hill GA and surrounding areas. Check out what some of our customers are saying about A/C Solutions Heating & Air Conditioning Heating and Air Conditioning services.
for Sugar Hill, GA
Great family owned business.
Lori - Sugar Hill, GA
Kind, conscientious, competent, friendly... I could go on. Thoroughly satisfied with my first exposure to A/C Solutions. I will see them again in Spring when I sign up for their maintenance plan. Customer Service done right!
Penny - Sugar Hill, GA
Linda - Sugar Hill, GA
Robin - Sugar Hill, GA
Okay. I rarely give reviews on anything, but I couldn't pass up this opportunity to rave about AC Solutions. We have been looking for a dependable company to service our AC and Furnace units for quite sometime, but have been disappointed time and time again, either due to service, knowledge or price. AC Solutions came out to investigate and possibly replace a part, which I was told by another company that we needed and it would cost me close to $550 to repair. AC Solutions looked over the unit thoroughly, and found that it was just a $25 vacuum hose. They also waived the service call fee and did a $99 Cleaning instead. Chris and Chad were very professional and explained everything in great detail. They were very knowledgeable. I can't say enough positive things about this company. Thank you AC Solutions for saving me and family a lot of heartache and a great deal of money.
Great thorough service!
Emily - Sugar Hill, GA
Knowledgeable and Prepared
Kurt - Sugar Hill, GA
I had all my questions/concerns answered. They were quick to diagnose and were able to implement the changes on the spot.
Installing this new induce draft motor due to the old one having cracks in it. We are in or near this area on almost a daily basis. We are here to serve you and take care of your heating and air conditioning needs. We are a true family owned and operated heating and air conditioning business. We treat you like family because our family depends on you. We have some of the best reviews check out what our customers are saying about us.
Performing cooling check on this 16 year old Tempstar central heating and cooling system. Replacing thermostat with a new Pro1 701 that has a 5 year warranty. Also replacing weak contactor and capacitor. Chemical flushing condenser coils and checking freon readings.
Customer wanted a second opinion on this Amana unit due to it not cooling. Another company said the evaporator coil was leaking and it needed replacing under warranty. After our diagnosing of the problem we found the the TXV has went bad. The customer also has a parts and labor warranty through Amana so that cut their out of pocket cost in half. Had someone changed the coil under warranty they would have had to pay for the coil since there are no leaks present.
Performed maintenance on this dual fuel heating and air conditioning system. Found that whoever installed didn't wire it correctly. There isn't a dual fuel board to correctly operate the heat. The burner and heat pump should never run at the same time. This will cause a compressor failure.
A/C not working for this couple. Performed air conditioning system check, changed 16x25x1 pleated filter, found system low on freon, changed weak 35+3 dual capacitor and single pole high voltage contactor, chemical flushed condenser coils, added 2.62 R-22 freon, rechecked freon and superheat